**Loading of any transmission line depends on,**

- Thermal limitation (I
^{2}R limitation) - Voltage regulation
- Stability Limitation

This is defined as the load (of unity power factor) that can be delivered by the line of negligible resistance.

Where V_{LL} is the receiving end voltage in kV and Z_{o} is the surge impedance in ohms, and SIL is the surge impedance loading or natural loading of the line

The above expression gives a limit of the maximum power that can be delivered by a line and is useful in designing the transmission line. This can be used for the comparison of loads that can be carried on the transmission lines at different voltages

From the above expression power transmitted through a long transmission lines can be either increased by increasing the value of the receiving end line voltage (V_{LL}) or by reducing the surge impedance (Z_{o}). Voltage transmission capability is increased day by day, this is the most commonly adopted method for increasing the power limit of the heavily loaded transmission line. But there is a limit beyond which is neither economical nor practical to increase the receiving end line voltage

By applying some methods such as introducing series capacitors (capacitors in series with the transmission line) or shunt capacitors (capacitors in parallel with transmission lines) can be used to reduce the value of surge impedance (Z_{o}).

Surge Impedance Loading (SIL) can be increased by reducing the Surge impedance of the line. From the above expression Z_{o} can be decreased by either increasing the capacitance (C) of the line or by reducing the inductance (L) of the line. Inductance (L) of the transmission line cannot be reduced easily

By use of the series capacitors surge impedance (Z_{o}) and the phase shift get reduced due to decrease in the line inductance (L). This improves the system stability limit. These capacitors also helps in reducing the line drops and so voltage variations. But this method causes difficulty under short circuit conditions of system as capacitors will get damage.

By use of shunt capacitors though the surge impedance (Z_{o}) is reduced but the phase shift of the system increases this affects the poor stability in the system specially when synchronous machines are under the load. This method is not employed in long transmission lines specially when stability limits are present

### Related Articles :

#### Engineering Tutorial Keywords:

- surge impedance of transmission line
- surge impedance loading of transmission line
- transmission line surge impedance loading research gate
- surgre impedance loading and power-transmission capability revisted
- surge impedance of HVDC cables
- surge impedance loading of high voltage power cables
- surge impedance loading
- PSCAD surge impedance output
- IF THE SURGE IMPEDANCE LOADING LEVEL FOR A 200 MILE TRANSMISSION LINE IS 200MW WHAT IS THE SURGE IMPEDANCE LOADING FOR AN IDENTICAL LINE THAT IS 400 MILES LONG
- does surge impedance loading depends upon size of conductor?

## No comments